Read our reviews to find out why your neighbors in Clarksville MD call us first when they need trusted recommendations from the professionals.
for Clarksville, MD
Our Reviews by City
Service call requested by customer for through the wall heating package not cooling or heating. Upon inspection from service technician, found low refrigerant levels and oil around compressor. Performed leak search and found small leak at a factory braze joint where the high side charge line meets the compressor discharge line. Recovered refrigerant and brazed leaking joint. Evacuated system and refrigerant measured at correct volume. Ran system to test. Through the wall heating and cooling system now working well. Customer very happy with service and purchased preventative maintenance program.
Advanced Heating & Cooling is fully licensed and insured
Master MD HVAC licensed and insured Master MD Gas Fitter Stationary Engineer IGSHPA Certified installer (International Ground Source Heat Pump Association) LEED Accredited Professional (Leadership in Energy and Environmental Design) NATE certified (North American Technical Excellence) Factory Trained Technicians