Read our reviews to find out why your neighbors in Essex MD call us first when they need trusted recommendations from the professionals.
for Essex, MD
Our Reviews by City
Commercial customer requested repairs to rapid unit. Picked up & installed new pressure transducer tubing to replace the existing clogged tubing. Checked operation and output of pressure transducer and verified operation through tech support. Found outdoor air damper linkage missing its set screw which allowed actuator to rotate but did not engage damper shaft so outdoor air damper would not open in relation to pressure transducer command. Removed actuator to reassemble and installed a set screw in the linkage Also found that at some point in the past an access hole had been cut into the top of the duct , which was at the highest point in order to be able to see the damper position for the main shop. When the access door was closed, a piece of wood was used to hold screws in, this piece of wood was not allowing dampers to open. The wood was completely dry rotted and appears to have been there for many years. I removed the wood opened the dampers and used cold weather foil tape to
Customer called and requested service call for leaking gas boiler. Service master technician recommends replacing old faulty gas boiler. Customer approved proposal and purchased Carrier Performance 90 gas boiler. Installation was successful. Customer also requested new thermostat for better efficiency in home. Customer purchased carrier performance thermostat and is very happy. customer will refer to al of his friends based on excellent workmanship and quality of system.
Advanced Heating & Cooling is fully licensed and insured
Master MD HVAC licensed and insured Master MD Gas Fitter Stationary Engineer IGSHPA Certified installer (International Ground Source Heat Pump Association) LEED Accredited Professional (Leadership in Energy and Environmental Design) NATE certified (North American Technical Excellence) Factory Trained Technicians