for Monkton, MD
Our Reviews by City
Radiant floor heat not working in family room. Checked boiler, pumps, zoning controls, manifolds. Complicated system with 6 hydronic zones that are radiant floor, radiators, and forced air. Some zones not marked. Boiler running well and most zones heating well. Found a few circuits of radiant floor not flowing to Family room zone. Adjusted flow to full flow for that zone. Set thermostat for forced air heat back 3 inches from radiant stat in family room. Forced air Thermostat is near a leaky outside door causing it to run more than radiant in family room. Advised customer to seal up door and also how to set temps and radiators for comfort. Customer will purchase preventative maintenance program. customer gave Advanced Heating & Cooling a 5 start rating and will recommend to all of her friends and neighbors.
Customer requested prevenatative maintenance. Cleaned electronic air cleaners. Cleaned drains. checked wiring, caps, contactors, zoning, condensate pump. Drain on 1st fl unit slow, cleared. All else ok. Cleaned coils. Ran units in cool. 1st fl comp 17.16a, air dt 17 deg. 2nd fl comp 12.96a, air dt 19 deg. Recommend wet switches for both units. Also found boiler storage tank leaking and should be replaced. Replacements completed. customer very happy and will recommend to all friends at work and at church and neighbors.
Advanced Heating & Cooling is fully licensed and insured
Master MD HVAC licensed and insured Master MD Gas Fitter Stationary Engineer IGSHPA Certified installer (International Ground Source Heat Pump Association) LEED Accredited Professional (Leadership in Energy and Environmental Design) NATE certified (North American Technical Excellence) Factory Trained Technicians