How do we know? The reviews from your Sparks Glencoe MD neighbors say it all.
for Sparks Glencoe, MD
Our Reviews by City
Found outdoor heat pump unit condenser frozen. Melted ice. Found defrost control not operating. Defrost control and sensor need to be replaced. Refrigerant pressures appear to be correct at 30° outdoor temp. Replaced defrost board and sensor. Tested system operation in heating. All amps good. Air filter needs to be changed. System shows age/wear. Contact is burned and pitted and should be replaced soon. Capacitor holding charge, if not replacing unit in the spring, recommend replacing dual capacitor. Outdoor coil should be cleaned in spring. Outdoor fan motor has rust on the housing, but working at this time. System working at this time.
Advanced Heating & Cooling is fully licensed and insured
Master MD HVAC licensed and insured Master MD Gas Fitter Stationary Engineer IGSHPA Certified installer (International Ground Source Heat Pump Association) LEED Accredited Professional (Leadership in Energy and Environmental Design) NATE certified (North American Technical Excellence) Factory Trained Technicians