How do we know? The reviews from your Towson MD neighbors say it all.
for Towson, MD
Our Reviews by City
Customer requested service due to noisy coil. Checked operation on unit to investigate report by customer that there is a noise coming from the unit like something is out of balance or possibly loose. Inspected the blower compartment, blower housing and monitored the blower wheel while the unit was running. Cycled the unit on and off to watch it start from a stopped position. Service tech did not see hear anything out of the ordinary, no sign of vibration or rattling or anything loose. I also went to the outdoor unit and cycled that unit on and off a few times, there is nothing abnormal with the outdoor unit either. The house is very quiet, the unit is in the attic and sitting directly over the guest room where the noise is being heard, I believe it is just the normal sound but is carrying through the return and is causing it to be heard. Customer satisfied with diagnosis and will highly recommend Advanced Heating & Cooling.
Customer called because there is no heat on first floor. Customer has water furnace water source heat pump. Closed loop running at low pressures. Technician added 40 psi. Leak test done and no leaks found. Problem was resolved completely. Customer very happy with Advanced Heating & Cooling.
Customer called for preventative maintenance. Master service technician cleaned electronic air cleaner. Treated condensate pump with pan tabs. Tested condensate pump operation. Cleaned steam humidifier. Tested humidifier/drain operation. Set humidistat to 40%. Provided and changed dehumidifier air filter and tested operation (left spare on site). Checked operation of UV light. UV bulb should be replaced on spring/summer pm. Checked gas 90% Lennox furnace operation. Cleaned condensate drain and trap. Checked drain operation. Cleaned flame sensor. Checked all wire connections. All amps on all motors good. Blower capacitor holding charge. Blower wheel clean. Gas pressure good. Heat exchanger in working condition. Checked flue vent pipe operation. Temp rise is 52°. System working well at this time. Recommend installing one or two water alarms in room. This would alert anyone if anything starts leaking (I.e. water, furnace, humidifier.
Customer called for service on filter for for tankless hot water heater. Service technician checked water heater operation. Heater only goes into high fire when water flow is over 7 gallons per minute. Checked hot water in master bedroom. Ran hot water heater with four different faucets and gallon per minutes was at 6, but water temp drops to below 99° and continues to fall. At colder outside temps the water heater may have a hard time maintaining a 140° temp due to cold street water temp. House has 5 full bathrooms. 2-1/2 baths. 2 laundry rooms and a kitchen. Problems seem to stem from water flow rates and design issues. The manufacturer of water heater is out of business. Recommend replacement of tankless hot water heater. Customer very satisfied with prompt courteous service. Customer will make decision on replacement. Customer will highly recommend Advanced Heating & Cooling.
Customer called to get service for oil line leak. Service technician found oil seeping from two spots. Repaired copper tubing on those two spots. Tested oil line and re-checked for leaks. None found after 1 hour after repair. Tested furnace and heat pump and oil fired water heater after repairs. System working well now. Customer very satisfied with technician services. Will highly recommend.
Water on floor by wine chiller- checked operation of wine chiller. Both filters clean. Checked condensate drain and pan, both clean and working. Checked operation of condensate pump. Pump is working. Both pressures and delta T where set to manufacturer specifications. Checked operation of steam humidifier. Humidifier working. Checked humidifier for any leaks. None found. Could not find the source of water being on the floor. The water may have come from condensation from the wine chiller duct work, there was a spot that the insulation had come off of the duct work. Reinstalled insulation. Cleaned up water. Placed a pan under duct work to see if that is where the water is coming from. Water could also have leaked through basement w
Customer called for service on existing carrier 90+ gas furnace due to no heat on first floor. Service tech replaced draft inducer and pressure switch. Tested furnace and all ok now. Preventative maintenance package was also purchased by customer. Customer satisfaction rating was a 5 star rating.
No heat upon arrival from Rheem oil furnace. Test bleed port to verify oil flow and strainer\filter is not clogged. Remove gun and noticed black burn marks on electrodes. Tested and verified transformer operation. Remove nozzle. Replace nozzle and electrodes from truck stock. Adjust and set electrodes. Unit is operating properly and efficiently.
Advanced Heating & Cooling is fully licensed and insured
Master MD HVAC licensed and insured Master MD Gas Fitter Stationary Engineer IGSHPA Certified installer (International Ground Source Heat Pump Association) LEED Accredited Professional (Leadership in Energy and Environmental Design) NATE certified (North American Technical Excellence) Factory Trained Technicians